Hanging furnace manufacturers debugging preparation steps before ignition
Date of publication：2019-06-10 Authors:佑玛 Click:
Timely replacement of old radiator in the heating season is not hot, weld or severe joint filler, the surface deformation, and the style of old still will use radiator, should find radiator professional installation personnel to inspect and repair, if necessary can replace a new set of radiator as soon as possible. For extended use of the radiator radiator and energy saving, environmental protection, in a timely stop warm period to replace. Change to choose high safety, energy conservation, environmental protection, and who used life long radiator. Wall hanging furnace manufacturers radiator clean method: after a heating period, gap and dust on the surface of radiator on oil, less health, so you need to clean the radiator and cleaning. Clean the radiator surface, please use the soft towel or brush, do not use any kind of organic solution, can be used daily detergent, weak alkaline soap and water, etc.
Floor heating equipment should be timely clean geothermal heating for convenient, beautiful and other characteristics, has become the choice of many families. Stop heating, floor heating equipment requires all aspects of maintenance. Wall-mounted boiler manufacturers to warm the water in the tube loop for a long time, the water contains a lot of the microbes, cb China merchants to join under certain conditions can produce a large number of biological mud, pipe wall will have a lot of mud, bacteria and scale, after a long time will affect the floor heating system of heating temperature, serious when still can have the possibility of congestion. Therefore, fortunately stops heating floor heating pipe for a thorough cleaning, timely formed in the line of the dirt, thoroughly remove impurities and bacteria. In order to prevent the formation of sediment in the pipeline pipe embolism.
Debugging preparation before ignition operation steps:
1, installation, commissioning, and for the first time the ignition must be conducted by professionals.
2, when home users use gas type, gas pressure, the use of the power supply must be consistent with that of cb, the size of the room and wall hanging furnace power should be matched.
3, check the pipeline and heating water system connection, ensure the machine interface and heating pipe connection is correct.
4, confirm the cb if input voltage is 220 v ~ 50 hz, electrical connection is correct, and have reliable grounding.
5, automatic open the exhaust valve and exhaust valve in the heating system,
Cb 6, open the water inlet valve and the system of water supply and return water pipe on the valve;
7, when water flowed from exhaust valve, close the discharge valve;
8, when the heating cycle system pressure is 0.15 MPa, shut off the water inlet valve wall hanging furnace;
9 in cb, start
10, because there are air system memory can cause noise in the runtime, this time can be repeated start hanging furnace, cb system in the air from the built-in automatic exhaust valve discharge. As the air discharge in the system, the system pressure will decline, at this time, but after being hanging furnace cooling, filling water again, and open the exhaust valve object completely.
11, if there will be short of pressure, water shortage in without dripping, running water, filling water again, until saturated water in the system.